This will be done, when the unit is in partial isolation or full shut-down provided vaccum pump should run and to arrange steam passing
We do critical valve leak testing inspection by Helium Leak Testing
In thermal power plants , we carry out Hydrogen cooled generator leak identification either unit is offline/ online, we will also undertake stator conductor inspection when the unit is offline. Our Engineers are well trained in carrying out the test and to interpret the results accurately. The job will be carried out by ASNT Level II Certified Engineers.
Arudra Engineers introduces a state-of-the-art inspection technique to detect leaks in the negative pressure parts of Steam Condensers,.Air-in-leakage is one of the worst obstacles of the Condenser's vacuum system, which undermines the performance of the equipment.Air-in-leak results in blanketing tube surface from the steam side thereby reducing heat transfer efficiency, as air is a bad conductor of heat. Also the back pressure increase due to air in leakage causes an increase in dissolved oxygen in the condensate resulting in deposition in water wall and super heater tubes of the Boiler, turbine blades thereby leading to generation loss, extra fuel consumption etc.
Hence an early detection of leaks and arresting them would definitely improve the performance of the condenser. It is very important that the negative pressure part system of the condenser / turbine should not be neglected at any cost.
We follow highest safety Standards, HSE policy and job will be carried out by ASNT LEVEL II Certified Engineers and Detailed Service Report Will Be Issued after the job completion.
Our procedure involves spraying of a tracer gas – Helium on all the suspect areas. Helium being a lighter gas than air, gets sucked into the system due to difference in pressure in case a leaking spot is present.
Helium which got sucked into the negative side of the Condenser is then sucked out through the air removal system along with the non-condensables and a sample of this ejected mixture is passed through our Mass Spectrometer to identify presence of Helium.
As the Spectrometer is extremely sensitive, even minute leaks can be identified instantaneously.
We will categorize the leaks as Small, Medium, Large and Very Large. This classification will help in planning the maintenance program.
# 79, Valmiki Street, Thiruvanmiyur, Chennai 600041, INDIA
Mr. M. Subramanian – Asst. General Manager (Mb. No. +91-9445003620)
Mr. R. Chandra Mohan – Sr. Manager (Marketing) (Mb. No. +91-9445003621)
Mr. A. Shunmuganathan – Sr. Manager (Mb. No. +91-9445003622)